Tel.: +7 (812) 331-96-20
Customer: Gazpromneft-Hantos Ltd.
Range of works for installation of two sets of "starting device of fast automatic reserve switching-on" at substations without change of existing high voltage commutation elements.
In 2010 SPA Saint-Petersburg Electro Technical Company, LLC implemented a project at the enterprise Gazpromneft-Hantos Ltd., which is one of main production affiliates of JSC Gazprom Neft. Main area of activities - petroleum production.
According to the Customer's terms of reference, operation time of fast automatic reserve switching-on had to be maximum 0.1s.
Performed production testing showed that full time of FARS device switchover (from the beginning of the short-break power supply up to full voltage recovery on the emergency input section) was 0.06 s.
Analysis of performed production testing permitted to the Customer to draw a positive conclusion about implemented device FARS-6kV at substation KUST-10.
Manager: Alexander Kvitnitsky